Q. Should I use a bypass damper on an Energy Recovery Wheel?
A. We typically use a bypass damper around a energy recovery device for frost control and economizer. That is typical for Heat Pipes and plate exchangers. In the case of an Energy Recovery Wheel we typically slow the wheel down to minimum speeds to allow for both frost control and economizer.
Bypassing the wheel in economizer would be less pressure drop and could create savings. The problem is that the unit casing has to grow to accomplish this. After careful study we have found that it is not cost effective to make the Energy Recovery Unit casing larger just to install a bypass for the wheel.
This design is incredible! You certinly
know how to kdep a reader entertained. Between your witt
and your videos, I was almost moved to start my own blog
(well, almost…HaHa!) Excellent job. I really enjoyed what
you had to say, and more than that, how you presentedd it.