Q. What is a typical pressure drop across the Konvekta coils?
A. The air pressure drop across the coils depends on several factors: number of rows, air face velocity, fin spacing and tube alignments. There is a trade-off between thermal efficiency and air pressure drop which will be one of the design considerations if we know the price of heat ($/MBTU) and the price of electricity (fan power). Typically, one can expect an air pressure drop in the range of 0.4″ to 0.7″.
Rudolf Zaengerle, Ph.D.
President, Konvekta USA Inc.
5 Independence Way, 3d Floor #95
Princeton, NJ 08540
Phone: 724 462 8207
More questions about Pumped Glycol Energy Recovery Systems, askRick?